Some Thai constant wire cable leakage risk due to recall today
Some Thai constant wire cable leakage risk due to recall dxdlabc P month today, areas of qinghai province bureau of quality and technical supervision for the production of wire and cable products in the product quality supervision and spot checks at the provincial level, enterprises production batches of the product is unqualified, fraction defective.
%, including qinghai's constant cable co. , LTD. The two batches of power cable products.
Recently, the company put on record the recall plan, decided to recall the unqualified products: (date) (month) (year) in the production of cross-linked polyethylene insulated PVC sheathed power cable (
And on the production of PVC insulated power cable (
The product for insulation shrinkage experiment, sheath weightlessness experiment and average thickness of insulation, insulation thickness of the thinnest place experimental projects do not conform to the requirements of the national standard, belong to the defective product.
Cable insulation quality not up to standard will lead to cable easy destroyed by the external force in the installation process, and reduce its ability to withstand various types of corrosion, easy to make a charged conductor is exposed to the environment, leading to leakage accidents.
Among them, wire and cable insulation heat shrinkable is unqualified, is due to material crosslinking degree is insufficient, can make the insulating material under certain conditions (
Such as cable in the process of operation, temperature rise)
Intensity is lower, affect the use of safe.
Qinghai's constant cable co. , LTD. , established in (date) (month) (year), the registered capital of ten thousand yuan, business scope: wire and cable processing and sales;
Aluminum, copper, aluminum sales.